Thank you. Photo 1 passed inspection for the plumbing, it was the framing damage that required him to redo it. I assumed he was using the vent for the washer dryer like a stack (the middle pipe extends to the roof) Not ok? Photo 3 passed inspection but with a note that said A.A.V. and S trap, so I guess the inspector noticed the lack of vent this time. I guess he wants the AAV due to lack of vent, but why would he call for an S trap? As for the cleanout, I haven't seen a single cleanout in the rough plumbing. Should I be concerned? By the way this is a slab house in Florida.
each fixture has to be vented PERIOD if you call him back he will red tag you again
no vent no clean out, drain for laundry sink needs to be 2'', looks like it is 1/1/2' laundry sink is 2 fixture units, minium drain is 2''
Have you ever really wondered about the process that water goes through to remove all of its pollut
The design team at Mosby Building Arts share their thoughts on emerging St. Louis bathroom trends,
Here is a common and yet seemingly complex Tenafly plumbingaproblem for you. You turn on your showe
With the State of California experiencing one of driest years in 119 years , water preservation is
Making the decision to replace your aging air conditioning and heating system for your home isn?t e
What You Need To Know About Indoor Air Pollution in Atlanta Every single day, we take in about 7 t
3 in. ABS DWV 22-1/2 Degree SPG x Hub Street ElbowBrand :- Other Price :- $5.84
1-1/2 in. ABS DWV Hub x MIPT Male AdapterBrand :- Other Price :- $1.63
3/4 in. Furniture Grade PVC 4-Way Tee in White (8-Pack)Brand :- Formufit Price :- $16.80
1/2 in. PVC Compression CouplingBrand :- Homewerks Worldwide Price :- $2.76